Outdoor floor-standing prepaid metering device
Floor type boundary switch integrated prepaid metering device is a column on the high-voltage metering, switch, control box to cabinet structure of the product, by the whole pouring dry type high-voltage metering box and ZW32F type intelligent boundary switch combination, the box is made of stainless steel or iron plate spray plastic material. This product is easy to install on the structure, beautiful appearance, the high voltage part is completely isolated from the low voltage meter room, and the high voltage room can not open the door operation under the condition of the equipment live, only in the case of power failure can the high voltage room door open, safe and reliable. The product occupies small area, is the living area, the industrial and mining enterprise and the box type change matching uses the perfect combination product. Personnel can directly open the door to view the bottom of the table and on-site operation switch action. The transformer adopts vacuum pouring of fully enclosed epoxy resin, so the aging problem is eliminated. The dividing switch part adopts vacuum switch with zero sequence and protection current transformer, and realizes zero sequence, overcurrent and quick break protection with intelligent controller, which can automatically remove single phase grounding fault and automatically isolate phase short circuit fault. To ensure the safety of non-fault users. This product has the FTU function to realize the switch remote control switch opening and closing; also has the GPRS remote control function (for details, see the following “Intelligent Controller Instructions “)
Normal operating conditions
a. Altitude does not exceed 3000m; pollution level: level Ⅳ.
b. Ambient air temperature: -40℃~+40℃; daily temperature difference: daily variation 25℃.
c. The wind speed is not more than 35m/s; the seismic intensity is not more than 8 levels.
d. There is no flammable, explosive danger, chemical corrosion place.
GB763-90 “Fever of AC high-voltage electrical appliances during long-term working hours”
GB1207-1997 “Voltage Transformer”
GB1208-1997 “Current Transformer”
GB17201-1997 “Combined Transformer”
GB4208-93 “Enclosure Protection Level”
GBJ63-90 “Code for the design of electrical measuring instruments of electric power installations”
DL/T448-2000 “Management Specification for Electric Energy Metering Device”
DL/T566-95 “Technical Conditions of Voltage Loss Timer”
JB5777.2-91 “General Technical Conditions for Control and Relay Protection Panels (Cabinets, Tables) for Secondary Circuits in Power Systems”
GB/T11022 “Common Technology of High Voltage Switchgear and Control Equipment Standard”
JB5777.3-91 “Basic Test Method for Control and Relay Protection Screen (Counter) for Secondary Circuits of Power System”
DL/T593-96 “Technical conditions for common ordering of high-voltage switchgear”
GB/1984 “AC High Voltage Circuit Breaker”
GB/T11022 “Common technical standards for high-voltage switchgear and control equipment standards”
GB311.1 “Insulation coordination of high-voltage power transmission and transformation equipment”
GB/T16927.1 “Part 1 of High Voltage Test Technology: General Test Requirements”
GB3309 “Mechanical test of high-voltage switchgear at room temperature”
GB311.1-1997 “Insulation coordination of high-voltage transmission and transformation equipment”
SD109 “Verification Regulation of Electric Energy Metering Device”
Floor-type intelligent prepaid high-pressure measuring box
①Meter box ② Lightning arrester ③High-pressure measuring box ④Protection current transformer ⑤Vacuum switch ⑥ Outgoing side
Note: This product is a non-standard product, can be customized according to customer requirements