Special Price for Generator Switchgear - HXGN17-12 box-type fixed AC metal-enclosed switchgear – AGP Electrical
Special Price for Generator Switchgear - HXGN17-12 box-type fixed AC metal-enclosed switchgear – AGP Electrical Detail:
HXGN17-12 box type fixed AC metal closed switchgear (ring cabinet) is rated voltage 12 kv..AC high-voltage electrical equipment with a rated frequency of 50 Hz is mainly used in three-phase AC ring network, terminal distribution network and industrial electrical equipment, which plays the role of receiving, distributing electric energy and so on. It is also suitable for equipment into box type substation.
Use of environmental conditions
♦ Ambient air temperature: -15℃ ~+40℃;
♦ Altitude: 2000m and below;
♦ Humidity condition: daily average value is not more than 95%, daily average value of water vapor pressure is not more than 2.2kPa; monthly average value is not more than 90%, monthly average value of water vapor pressure is not more than 1.8kPa.
♦ Earthquake intensity: no more than 8 degrees;
♦ No corrosive or flammable gas and other obvious pollution places.
Note: When the above normal use conditions are exceeded, the user can negotiate with our company.
Main technical parameters of vacuum circuit breaker
|2||1min power frequency withstand voltage||kV||Ground and interphase 42; isolation fracture 48|
|3||Lightning impulse voltage (peak)||kV||Ground and interphase 75; isolation fracture 85|
|5||Main bus rated current||Hz||630|
|6||Load switch||Rated current||A||630|
|7||Rated current power down life||A||Not less than 100|
|8||Breaking no-load transformer capacity||kVA||1250|
|9||Rated thermal stability current||kA/s||20/4; ground switch 20/2|
|10||10 Rated dynamic stable current (peak value)||KA||50|
|11||Rated short-circuit making current (peak value)||Times||50|
Main technical parameters
|12||Fuse rated current||A||100|
|13||Rated transfer current||A||1500||2000|
|14||Rated short circuit switching current combination||kA||Terrestrial and interphase 75; isolated fracture surface 85|
|17||Auxiliary circuit 1 min power frequency withstand voltage||kV||2|
|18||Working Voltage of Electric Operating Mechanism||V||AC/DC 220;110|
|20||Shape dimensions (width X depth X height)||mm||650(850)X900X2000(2200)|
Use and troubleshooting
♦ packaging, storage and transportation
◊ ring net cabinet is packed in single wooden box when it leaves the factory. tipping, inversion and violent vibration are not allowed during storage and transportation. It is not allowed to push and pull directly on the ground when moving; when there is no lifting device, the cylinder can be cushioned under the packing box sleeper to make it slide to the installation position.
◊ prevent the cabinet from rain and moisture.
◊ ring net cabinets should be placed in a well ventilated place and can prevent all kinds of harmful gases from invading. It is strictly forbidden to store in a warehouse with chemicals, acid and alkali, etc.
◊ check if the package is damaged before unpacking, pay attention to protect the product when unpacking.
2.2 Inspection of the appearance of the cabinet body; at the same time check whether the components in the cabinet are damaged and whether the fittings are in accordance with the packing list.
◊ check if random files are safe.
a、 product instruction manual and each component instruction in cabinet;
b、 factory test report;
c、 product certification;
d、 packing list;
e、 secondary wiring diagram.
Installation and commissioning
♦ Place the ring network cabinet on the installation foundation during installation, arrange it neatly and debug it, and then fasten it with fasteners.
♦ When installing the main bus bar, open the bus bar room for installation. The contact surface of the connecting bus bar should be flat and free of dirt.
♦ The grounding of the ring network cabinet should be reliably grounded, and the grounding should be checked for loops.
♦ When debugging, follow the instructions of the ring network cabinet and the instructions of each component in the cabinet for debugging.
♦After installation and commissioning, operate the respective switching elements and anti-misoperation mechanism 5 times. If no abnormal phenomena are found, the switch is considered to be operating normally.
Use and troubleshooting
♦ Check before power on
The ring network cabinet shall comprehensively check the electrical performance, insulation level and wiring correctness of all components in the cabinet before power transmission, and check that everything is normal before it can be put into operation.
♦ Normal operation state
During normal operation, regardless of the incoming or outgoing cabinet, the load switch should be in the closing position, the grounding knife should be in the open position, and the cabinet body should be in the closed and locked state.
◇When the incoming cabinet is faulty and repaired, the incoming power supply should be cut off first, the load switch should be opened, and the live display on the cabinet should be checked.
Carry out maintenance.
◇When the outlet cabinet is overhauled, the load switch in the cabinet should be disconnected, the grounding knife should be closed, and the front door should be opened for maintenance. At this time, the main busbar is in a live state.
Maintenance and repair
♦ The ring network cabinet needs to be maintained and repaired under the following conditions;
a. Check the insulation level of the product after 5 years of operation;
b. After the load switch has been opened 100 times, the main circuit resistance, the work of the load switch, the static contacts and auxiliary contacts should be checked.
♦ In general, the ring network cabinet should be maintained and overhauled after a power outage.
Product detail pictures:
Related Product Guide:
To meet the customers' over-expected pleasure , we have now our solid crew to supply our greatest all round assistance which includes marketing, sales, planning, production, top quality controlling, packing, warehousing and logistics for Special Price for Generator Switchgear - HXGN17-12 box-type fixed AC metal-enclosed switchgear – AGP Electrical , The product will supply to all over the world, such as: Hyderabad, Argentina, Argentina, Our stock have valued 8 million dollar , you can find the competitive parts within short delivery time. Our company is not only your partner in business, but also our company is your assistant in the coming corporation.
By Teresa from Argentina - 2018.02.12 14:52
This manufacturer can keep improving and perfecting products and service, it is in line with the rules of market competition, a competitive company.
By Jill from Salt Lake City - 2018.06.26 19:27